Overhead Cooler Fan Motors
The images of these two motors are taken with the same parameters, scale, and level. They should be operating under the same conditions. The inset motor, however, has the wrong pitch of fan blade, at it is operating at least 10° C hotter. This surface temperature on the motor housing is indirect, and the air flow in the area will reduce the thermal signature to some degree, so this calculated temperature rise is conservative.